Aldi opts for R513A in Spanish store
SPAIN: Chemours’ lower GWP refrigerant replacement for R134a has been adopted for a new Aldi store in Dos Hermanas, near Seville.
Faced with a desire to reduce carbon footprints, lower energy consumption and comply wth the F-gas phase-down, European supermarkets are pursuing a number of alternative refrigerant options. These include modernising their central refrigeration systems, adopting low GWP and CO2 refrigerants, and integrating refrigeration and air conditioning systems.
For its new Dos Hermanas location, Aldi worked with Tewis Smart Solutions, a Valencia-based energy Consultancy specialising in designing integrated solutions for refrigeration and air conditioning installations.
The solution was to use R513A, a refrigerant devoted by Chemours and marketed as Opteon XP10. With a GWP of 573 it provides a 56% reduction in GWP compared to R134a. The use of Opteon XP10 was seen as the best option to meet the F-gas regulation without having to sacrifice capacity and energy efficiency.
“We chose Opteon XP10, because it offered the optimal balance of properties when compared to other replacement options,” said Javier Atencia, technical manager for Tewis.
The installation was said to have been seamless and occurred overnight with limited interruption to business activities. In total, three independent machines were retrofitted:
Refrigeration rack TN1 (30 kW): dairy shelf murals (-6 ºC)
Refrigeration rack TN2 (39 kW): meat, fish, fruit, vegetable, fourth range (fresh-cut products) and frozen food store units (-8 ºC)
Refrigeration rack AT1: air-conditioning for check-out area (+5 ºC)
In Winter, the condensation of TN1 and TN2 refrigeration racks is achieved through an AHU managed by controllers developed by Eliwell specifically for this application. Full recovery of the heat energy is achieved in winter mode.
The installation was carried out by Spanish contractor Friex, based in Don Benito, Badajoz.
While tests are still being carried out to determine the total cost savings associated with using R513A, previous Aldi installations using this refrigerant have shown increased energy efficiency compared to R134a.
Latest news from the world of air conditioning and refrigeration
UK: A cascade refrigeration system twinning CO2 with the HFO refrigerant 1234ze has been named as Retail Energy Project of the Year in last week’s Energy Awards in London.
UK: Industrial refrigeration contractor Stonegrove Refrigeration has appointed Steve Gowing as design and project engineer.
UK: Javac UK, the refrigerant recovery and vacuum pump supplier, has been named as Climate Centers’ Supplier of the Year for the second year running.
UK: Ruskin Air Management has been renamed Swegon Air Management following its acquisition by the Swedish manufacturer Swegon.
EUROPE: The European Commission has warned that the uptake of training in alternative refrigerants is too low to match the requirements of the F-gas phase down.
SOLOMON ISLANDS: Customs authorities in the Solomon Islands have reported their second seizure of the illegal CFC refrigerant R12 this year.
IRAN: German compressor manufacturer Bitzer has established a subsidiary company in Iran.
USA: Seven local residents are reported to be suing Honeywell after a chemical leak at its Geismar, Louisiana, plant in August.